Free Shipping Details
Free Shipping Policy excludes LTL Truck Deliveries and just a few oversized products. Click Here for more info
Example of how to pipe a Hydronic Radiator or Fan Convector with a Mono-Flo Tee. The Mono Flo tee will force water up into the applicance.
You will notice how the distance between the Mono Flow Tee and regular tee is about 12 inches or more - this is important. Also the Mono Flow Tee is on the return. In some cases you will need two mono flow tees for installs that are a long way from the pump - see more info on this on the mono flo buy pages.
Piping with one or two Mono Flo Tees
Quantity 1 or 2 - Heating Mono Flo Tees to Copper or PEX
Quantity X - Copper and Brass Fittings
Quantity X - Hydronic Fan Convectors
Quantity X - Hydronic Radiators
Quantity 1 - Sharkbite Fittings
Quantity X - Hydronic Heating Trim - such as Pumps, Zone Valves, Ball Valves, etc
X = Various Amounts of Product needed - dependant on actual system