Myson Twin Entry Bypass Valve - HV-A
- Angle - For Connecting T6 Radiators & Contractor Series - Compression or Pex Adapters Purchased Seperately
Product ID • HVA000000000
There are two very different connection options for the T6 radiators, and the instructions are separated in the booklet.
Bottom Center Connections: These connections must be used for the internal thermostatic valve to work. The inlet must be the left hand connection as you face the front of the radiator. For series connection (maximum 2 GPM), HV-A or HV-S bypass valves may be used.
Side Tappings: The T6 may be connected like a conventional panel radiator. This arrangement negates the effectiveness of the internal thermostatic valve. It will be necessary to cap the bottom center connections with brass caps. The TRV insert should be removed and replaced with one of the plugs furnished with the radiator.
Please Note: If you are using HV-A valve with Contractor Series Radiators, you must also order part number 102-82-53 – 1/2” to 3/4” adapters. Also, you will then need either part number 101-68-44 for 1/2” copper compression, or 164-68-50 for 1/2” Pex Compression. (Part # 102-82-53 is not needed for the Myson T6 Series Radiators)
Manuals & Docs
Info & Links