JJM Boiler Works - JM-3 PH Neutralizer Kit - JM-3 CLEAR
- 300 MBH - 3.45 GPH - Clear Tube
Product ID • JM3CLEAR0000
JJM Boiler Works - JM-3 CLEAR PH Neutralizer Kit maximum 300 Boiler Btu - 3.45 GPH - Clear Tube.
The pH measurement of a fluid is an indicator of the acidity or alkalinity. Neutral fluids have pH of 7.0. Acid fluids have pH below 7. And alkaline fluids have pH above 7 (up to 14). The pH can be easily measured using litmus paper.
Condensate pH from condensing boilers and furnaces is acidic. The condensate pH needs to be increased (made less acidic) to prevent possible damage to cast iron soil pipe, ABS pipe, septic tanks, plants, wastewater treatment plants and other materials handling waste water.
JM-series condensate neutralizing tubes increase pH and reduce acidity. Each increase of 1.0 in pH is a 10-times decrease in acidity. The pH of condensate is increased by approximately 1.0 to 3.0 after passing through NB neutralizing tanks. (This is a reduction in acid concentration of from 10 to 1000 times.)
Recharge tubes regularly. Tubes should be recharged when pH level moves below 6. The pH should be checked regularly (at least twice during the first year of operation) to determine the required recharging schedule.
This may require recharging as often as twice per year for high-usage systems, such as boiler systems equipped with indirect water heaters.
Boiler/furnace applications for space heating only (no DHW) may require recharging only once per year.
Manuals & Docs
JM Boiler Works jm-3 Condensate Boiler Neutralizing Tube Techs and Specs
- Maximum Boiler Btu
- 19 1/2 inches
- 2 3/4 inches
- 3 1/2 inches
- Inlet/Outlet Connections
- 3/4 Inches hose barb x 1/2 Inches NPT or 3/4 Inches PVC x 1/2 Inches NPT (both supplied)
Info & Links